Hand Cleaning Device UV Lamp Water Sterilizer
|FOB Price:||US $2,700 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $2,700/ Piece|
|Production Capacity:||150 Units Per Month|
|Payment Terms:||L/C, T/T, Western Union, Paypal|
- Model NO.: YLC-2000
- Type: Lightwave Disinfection
- Electric Tension: 220V
- Ultra High Temperature Alarm: Ultra High Temperature Alarm
- Material: Stainless Steel
- Tube: Quartz Tube
- Water Inlet Turbidity: Less Than 1 Ntu
- Water Inlet Manganese Content: Less Than 0.05 Mg/Liter
- Lifespan of UV Lamp: 9000 to 12000 Hours
- Water Output: 1 to 500 Cubic Meter Per Hour
- Transport Package: Plywood Case Into Container
- Origin: Jiangyin, China
- Theory: UV Light Sterilization
- Certification: CE
- LCD Display: With LCD Display
- Sterilization Information Recording and Printing: Sterilization Information Recording and Printing
- UV Light: UV-C 254nm Wavelength
- Water Inlet Hardness: Less Than 120mg/Liter
- Water Inlet Iron Content: Less Than 0.3 Mg/Liter
- Cleaning Model: Hand-Cleaning, Rod Cleaning, Automatic Motor
- Control System: Control Box, PLC, Remote Control, etc
- Trademark: YLD
- Specification: to be customized
- HS Code: 842121999
Ultra Violet Sterilizing Water Purification
Ultra-violet (UV) light kills disease-causing micro-organisms such asEcoli with a 99.9% effectiveness. UV sterilization adds nothing to, and removes nothing from the water and is extremely cost effective by volume. UV Water Sterilization technology seeks to use the same process as nature to provide drinking water that is completely safe.By exposing contaminated water to high intensity UV light, disease
causing micro-organisms are rendered harmless and the water produced is safe, clean and fresh.
In nature, the sun produces UV rays which have a germicidal effect on disease causing pathogens in water. When these contaminants are exposed to UV light, they are rendered harmless and the output water is considered disinfected. Additional water filters are available for any system to filter out sediments, odors, bad tastes water sterilization units will provide an adequate UV dose to kill the following contaminants among many others:
? Legionella Pneumophilia
? Mycobacterium Tuberculosis
How Ultraviolet Pool Sanitizers Work
SpectraLight is installed in-line just after your pools existing filtration system. SpectraLight bombards the passing water flow with a high intensity germicidal ultraviolet ray that destroys more than 60 waterborne pathogens, including algae, bacteria, cysts, and viruses. The UV sanitizing lamp is housed in an industrial graphite housing optimized for high flow rates. A highly specialized quartz glass sleeve protects the lamp from passing water while transmitting 99.9% of the UV light. The highly concentrated electromagnetic energy destroys organic matter and eliminates the formation of dangerous chlorine by-products called chloramines that commonly lead to red, stinging eyes, skin irritations, asthma and allergies. This energy penetrates the cell walls of bacteria, viruses, algae, cysts and all pathogens. That's right: no pathogen can escape a powerful dose of UV from a SpectraLight sterilizer.
Limitations in UV Water Filters
As remarkable as the technology is, ultraviolet water purification by itself is not enough to render water completely safe for drinking purposes. That's because UV radiation works only on microorganisms such as bacteria and viruses. UV light is of little use in eliminating other contaminants in water such as chlorine, heavy metals and VOC's (Volatile Organic Compounds).
VOCs are toxic, man-made chemicals that leach into ground water during the manufacture of products such as paints, petroleum products and refrigerants.
1.Food processing industry, including juices, milk, drinks, beer, practical oil and canned food.
3.Hospitals, various laboratory and high levels of pathogenic body water disinfection.
4.Households building, residential, office buildings, hotels, restaurants, water factories.
5.Purification and disinfection of shellfish, fish cleaning and disinfection
6.Military camp, field water supply system
7.Urban wastewater disinfection.
8.Swimming pool, other recreational water disinfection
9.Thermal power, nuclear power plant industrial, central air conditioning system cooling water.
10.Biological, chemical and pharmaceutical, cosmetics for the production of cooling water.
11.Sea water, fresh water breeding, aquaculture water
12.Agricultural water disinfection
Principle of Operation
UV water disinfection system design has been carefully conceived to provide adequate germicidal dosage throughout the disinfection chamber. The dosage, as it applies to UV disinfection, is a function of time and the intensity of UV radiation to which the water is exposed. Exposure time is related to the flow rate, the higher the flow rate, the lower the exposure time or the lower the flow rate, the higher the exposure time. The UV intensity is the amount of energy, per unit time, emitted by germicidal lamp. The Dosage is the product of UV intensity and the exposure time.
Limitation of Use
The UV water disinfection system NOT intended for the treatment of water that has an obvious contamination or intentional source, such as raw sewage, nor is the unit intended to convert wastewater to microbiologically safe drinking water.
Water Quality (in)
Water quality plays a major role in the transmission of germicidal UV rays. It is recommended that the water does not exceed following maximum concentration levels
Effectively treating water with higher concentration levels than listed above can be accomplished, but may require added measures to improve water quality to treatable levels. If, for any reason, it is believed the UV transmission is not satisfactory, contact the factory.
UV wavelength (nm)
DOSAGE is the product of intensity & time
dosage=intensity*time=micro watt/cm2*time=microwatt-seconds per square centimeter
Technical parameters sheet
1.Before install this equipment,please test the voltage for connection.normal running for UV lamp and ballast requires 240V.
2.There should be a 1.5 meter space for spared at each end(at least one end)for disassemble the quartz tube and UV lamp.then connect the water inlet and outlet
3.After connected the inlet and outlet pipe,then release the water to check whether there is any leakage at the nut connection.if it is leakage,screw the nut or check the sealing ring is cracked or not.pipe.please do not use too much force when screw the nut to avoid any cracking of tube.
4.The supporting frame must be grounding.
5.The UV lamp is inserted into the quartz tube through the nut with holes. the electric control panel is connected with 4-core plug and UV lamp. while connecting, two hands should handle the pin end and 4 core plug end respectively. Insert into plug slowly to avoid possible break-up because of corrosion.