Stainless Steel 304 Housing Ultraviolet Water Sterilizer
|FOB Price:||US $3,500 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $3,500/ Piece|
|Production Capacity:||150 Units Per Month|
|Transport Package:||Plywood Case Into Container|
|Payment Terms:||L/C, T/T, Paypal, Western Union|
- UV sterilizer
- 50 Products
- Product Image
- Product Name
- FOB Price
- Payment Terms
- Product Package
- Product Attribute
- Product Table
- Model NO.: YLC-1200
- Application: Industry
- Disinfection Method: Ultraviolet
- Tube: Quartz Tube
- Water Inlet Turbidity: Less Than 1 Ntu
- Water Inlet Manganese Content: Less Than 0.05 Mg/Liter
- Lifespan of UV Lamp: 9000 to 12000 Hours
- Water Output: 1 to 500 Cubic Meter Per Hour
- Specification: to be customized
- HS Code: 842121999
- Certification: ISO9001, CE
- Voltage: 110V/220V/380V
- UV Light: UV-C 254nm Wavelength
- Water Inlet Hardness: Less Than 120mg/Liter
- Water Inlet Iron Content: Less Than 0.3 Mg/Liter
- Cleaning Model: Hand-Cleaning, Rod Cleaning, Automatic Motor
- Control System: Control Box, PLC, Remote Control, etc
- Trademark: YLD
- Origin: Jiangyin, China
What is an Ultraviolet (UV) Pool Sanitizer?
Ultraviolet (UV) pool sanitizers utilize a cutting-edge, non-chemical process that uses germicidal UV light rays to sanitize water, air and surfaces that may be contaminated. Ultraviolet pool sanitizers emit a high intensity germicidal light ray that alters or disrupts the DNA or RNA of targeted organisms such as algae, bacteria, viruses, cysts and protozoa. The highly concentrated electromagnetic energy also destroys organic matter, eliminating the formation of dangerous chlorine by-products.
Where Did UV Sanitizers Get Their Start?
The UV light spectrum was discovered with the identification of light waves. Scientists have known for almost a century that UV is a powerful neutralizer of algae, bacteria and viruses. They also discovered that the optimal ultraviolet wavelength to destroy microorganisms was between 250 and 270 nm. The results led scientists to incorporate Ultraviolet sanitizer technology into sterilizing drinking water more than 30 years ago. Ultraviolet disinfection has since gained in popularity in drinking water and wastewater disinfection in the last 10 years. Now ultraviolet sanitizers disinfect a significant percentage of all drinking and wastewater. The big news is that New York City has designed the world's largest drinking water facility, capable of treating two billion gallons per day. New York will install twelve thousand ultraviolet lamps - the same type of lamps found in SpectraLight UV sanitizers.
UV sterilization affects waterborne contaminants and disease causing pathogens with a
99.9% kill rate. The result is high quality water exceeding all health department standards.
Factors Affecting UV Treatment:
Because UV does not leave any measurable residue in the water, it is recommended
that the UV sterilizer be installed as the final step of treatment and located as close as
possible to the final distribution system. Once the quality of the water source has been
determined, you will need to look at things that will inhibit the UV from functioning
properly (i.e. manganese, TDE, turbidity and suspended solids).
Iron and Manganese will cause staining on the quartz sleeve and prevent UV energy
from transmitting into the water levels as low as 0.03 ppm of iron and 0.05 ppm of manganese. Proper pre-treatment is required to eliminates this staining problem.
Total Dissolved Solids (TDS) should not exceed approximately 500ppm. There are many
factors that make up this equation, such as the particular make up of the dissolved solids
and how fast they absorb the available UV energy. Calcium and magnesium, in high
amounts, has a tendency to build up on the quartz sleeve, again impeding the UV
energy from penetrating the water.
Turbidity: is the inability of light to travel through water. Turbidity makes water cloudy and
aesthetically unpleasant. In the case of UV, light levels over 1NTU can shield microorganisms from UV energy, making the process ineffective.
Suspended Solids: need to be reduced to a maximum of 5 microns in size. Larger solids
have the potential of harboring or encompassing the micro organisms and preventing
the necessary UV exposure. Pre-filtering is a must on all UV applications to effectively estroy micro organisms to a 99.9% kill rate.
How Ultraviolet Pool Sanitizers Work?
SpectraLight is installed in-line just after your pools existing filtration system. SpectraLight bombards the passing water flow with a high intensity germicidal ultraviolet ray that destroys more than 60 waterborne pathogens, including algae, bacteria, cysts, and viruses. The UV sanitizing lamp is housed in an industrial graphite housing optimized for high flow rates. A highly specialized quartz glass sleeve protects the lamp from passing water while transmitting 99.9% of the UV light. The highly concentrated electromagnetic energy destroys organic matter and eliminates the formation of dangerous chlorine by-products called chloramines that commonly lead to red, stinging eyes, skin irritations, asthma and allergies. This energy penetrates the cell walls of bacteria, viruses, algae, cysts and all pathogens. That's right: no pathogen can escape a powerful dose of UV from a SpectraLight sterilizer.
1.Food processing industry, including juices, milk, drinks, beer, practical oil and canned food.
3.Hospitals, various laboratory and high levels of pathogenic body water disinfection.
4.Households building, residential, office buildings, hotels, restaurants, water factories.
5.Purification and disinfection of shellfish, fish cleaning and disinfection
6.Military camp, field water supply system
7.Urban wastewater disinfection.
8.Swimming pool, other recreational water disinfection
9.Thermal power, nuclear power plant industrial, central air conditioning system cooling water.
10.Biological, chemical and pharmaceutical, cosmetics for the production of cooling water.
11.Sea water, fresh water breeding, aquaculture water
12.Agricultural water disinfection
Technical parameters sheet
1.Before install this equipment,please test the voltage for connection.normal running for UV lamp and ballast requires 240V.
2.There should be a 1.5 meter space for spared at each end(at least one end)for disassemble the quartz tube and UV lamp.then connect the water inlet and outlet
3.After connected the inlet and outlet pipe,then release the water to check whether there is any leakage at the nut connection.if it is leakage,screw the nut or check the sealing ring is cracked or not.pipe.please do not use too much force when screw the nut to avoid any cracking of tube.
4.The supporting frame must be grounding.
5.The UV lamp is inserted into the quartz tube through the nut with holes. the electric control panel is connected with 4-core plug and UV lamp. while connecting, two hands should handle the pin end and 4 core plug end respectively. Insert into plug slowly to avoid possible break-up because of corrosion.