One Work One Standby Resin Regeneration Water Softener System
|1-9 10-19 20+|
|FOB Unit Price:||US $1,400 US $1,250 US $1,120|
|Purchase Qty. (Pieces)||FOB Unit Price|
|Production Capacity:||100 Units/Month|
|Payment Terms:||L/C, T/T, Western Union|
- Model NO.: YL-I-4A
- Control Valve: Manual,Automatic
- Water Hardness of Output Water: <0.03mmol/L
- Working Pressure: 0.2-0.5MPa
- Brand of Valve: Runxin,Fleck,Jk,etc
- Turbidity of Feed Water: <8ntu
- Transport Package: Plywood Case Into Container
- Origin: Jiangyin, China
- Material for Resin Tank: Gfrp,Ss
- Water Hardness of Feeding Water: <8mmol/L
- Working Temperature: 1-55 Centigrade
- Resin Material: 007*1 Strong Resin
- Iron Content in Feed Water: <0.1mg/L
- Trademark: YLD
- Specification: to be practical
- HS Code: 842121999
IntroductionIon exchange units that replace calcium and magnesium ions from water are known as water softeners. They may also remove varying amounts of other inorganic pollutants such as metals, but they will not remove organic chemicals, pathogens, particles, or radon gas. Water softener units work most efficiently with particulate-free water.
Principles of Ion Exchange to Soften Water
Calcium and magnesium ions are atoms having a positive electrical charge, as do sodium and potassium ions. Ions of the same charge can be exchanged. In the ion exchange process, a granular substance (usually a resin) that is coated with sodium or potassium ions comes into contact with water containing calcium and magnesium ions. Two positively charged sodium or potassium ions are exchanged (released into the water) for every calcium or magnesium ion that is held by the resin. This "exchange or trade" happens because sodium or potassium are loosely held by the resin. In this way, calcium and magnesium ions responsible for hardness are removed from the water, held by the resin, and replaced by sodium or potassium ions in the water. This process makes water "soft." Eventually, a point is reached when very few sodium or potassium ions remain on the resin, thus no more calcium or magnesium ions can be removed from the incoming water. The resin at this point is said to be "exhausted" or "spent," and must be "recharged" or "regenerated."
01. By means of Absorbing the calcium and magnesium ions in water with resin, since the hardness of water is mainly composed of calcium and magnesium, in general, we adopt cation exchange resin (softener), replace Ca2+, Mg2+ (main ingredients for scale) in water, as the increase of Ca2+ and Mg2+ in resin, removing performance on Ca2+, Mg2+ of resin will gradually reduce.
02. When the resin has absorbed a certain amount of calcium and magnesium ions, it must be regenerated, the regeneration process is that flush resin layer with the salt water in salt box, replace hardness ion out of the resin again, and discharged from the tank with waste liquid of regeneration, then resin resumed the function of softening and exchanging.
03. The principle of sodium ion exchange and softening treatment is to exchange cation in the raw water with resin, hardness constituents Ca2+and Mg2+ in water exchange Na+ in resin, thus absorb the Ca2+and Mg2+ to make the water to be softened.
2RNa + Ca2+ = R2Ca + 2Na+
2RNa + Mg2+ = R2Mg + 2Na+
After the water treated by sodium ion exchanger, the Ca+ and Mg+ were superseded by Na +.
Application of softener
Mainly used in industry and civil water softening preparation, such as Boiler feed water make-up water, air conditioning system make up water, heat exchanger, power plant, chemical, textile, printing and dyeing, bio-pharmaceutical, Electronic system and water pretreatment.
Softener equipment applies cation resin for softing raw water,its main target is to use cation resin to adsorp (main parts of ),encreasing the hardness of raw water.
1. Users can choose manual operation control system for saving cost.
2. If users using for 24 hours can accord to water using time choosing for rebirth.
it will be dual-tank water softener.
3. Uses can according to water quality requirement:first grade multi-media filter,which can remove mud,rust,colloid and suspension in water.Second grade activated carbon filter,which can remove color,olfactory,biochemistry organic in water and encrease the left oxygen value and pollution in water.Third grade equiped softener equipment.
4. Effluent water capacity achieves the water supply of national low-pressure bioler.
5. Time control- type;flow control- type.In working ,apply single-tank,double-tank and multi-tank etc. other varied combination method.When choosing,users can choose as their needs.In operation,it has not only automatic function,but also is manual operation.
Technoloty index and working
Hardness of raw water: <8mmol/L
Hardness of effluent water: ≤0.03mmol/L
water flow: 0.3-100 m3/hour
Control method: time or flow
Working electric: 220V/50Hz
System automatic water softener widely used in steam bioler,heating bioler,exchanger,air conditioner, and other systems water softener,also used in hotel,restruant,office, and other life water treatment and food,drinking,wine,washing,textile,chemical,medicine and other industrial softener water treatment.
Type I : Single-tank and single-valve( flow rate based control)
Type II.dual-tank and dual-valve, two tanks work simultaneously but regenerate at different time
Type III.:dual-tank and single valve,one work one standby
|Model||water output||Resin-tank<mm>||Brine tank|