Salt-Based Ion Exchange Softener with Dual Tanks and Dual Valve
|FOB Price:||US $1,800 / Piece|
|Min. Order:||1 Piece|
|Min. Order||FOB Price|
|1 Piece||US $1,800/ Piece|
|Production Capacity:||100 Sets/Month|
|Payment Terms:||L/C, T/T, Western Union, Paypal|
- Hot Product
- 49 Products
- Product Image
- Product Name
- FOB Price
- Payment Terms
- Product Package
- Product Attribute
- Product Table
- Model NO.: YL-II-15
- Working Principle: Ion Exchange
- Inlet Mode: Pipeline
- Material for Resin Tank: Gfrp or Ss304/Ss316
- Hardness of Effluent Water: ≤0.03mmol/L
- Operating Ambient Temperature: 1°c-55°c
- Iron Content: ≤0.3mgl/L
- Control for Regeneration: Time Based or Flow Rate Based
- Trademark: YLD
- Specification: to be practical
- HS Code: 842121999
- Installation: Vertical Type
- Certification: CE, SGS
- Heating Mode: Instant Heat
- Hardness of Raw Water: <8mmol/L
- Working Temperature: 0.25-0.6MPa
- Suspended Solids in Raw Water: ≤0.5mgl/L
- Relative Humidity: ≤95%
- Control Valve: Runxin,Fleck,Jk ,etc
- Transport Package: Plywood Case Into Container
- Origin: Jiangyin, China
Ion Exchange softener
Water softening happens through a process called ion exchange, which uses an ion exchange resin. The resin comprises of tiny polymeric beads which are specially formulated so that they can be charged with certain ions. Calcium and magnesium, the causes of scale and scum from hard water, are referred to as ions, and as water passes through the resin, the calcium and magnesium ions swap places with the sodium ions on the resin. Sodium salts, unlike calcium and magnesium, are highly soluble so sodium does not cause scale or scum. When all the sodium ions have been exchanged for calcium or magnesium, the resin must be regenerated by recharging it with sodium ions. This is done by flushing the resin with salt solution (brine).
01. By means of Absorbing the calcium and magnesium ions in water with resin, since the hardness of water is mainly composed of calcium and magnesium, in general, we adopt cation exchange resin (softener), replace Ca2+, Mg2+ (main ingredients for scale) in water, as the increase of Ca2+ and Mg2+ in resin, removing performance on Ca2+, Mg2+ of resin will gradually reduce.
02. When the resin has absorbed a certain amount of calcium and magnesium ions, it must be regenerated, the regeneration process is that flush resin layer with the salt water in salt box, replace hardness ion out of the resin again, and discharged from the tank with waste liquid of regeneration, then resin resumed the function of softening and exchanging.
03. The principle of sodium ion exchange and softening treatment is to exchange cation in the raw water with resin, hardness constituents Ca2+and Mg2+ in water exchange Na+ in resin, thus absorb the Ca2+and Mg2+ to make the water to be softened.
2RNa + Ca2+ = R2Ca + 2Na+
2RNa + Mg2+ = R2Mg + 2Na+
After the water treated by sodium ion exchanger, the Ca+ and Mg+ were superseded by Na +.
Softener equipment applies cation resin for softing raw water,its main target is to use cation resin to adsorp (main parts of ),encreasing the hardness of raw water.
1. Users can choose manual operation control system for saving cost.
2. If users using for 24 hours can accord to water using time choosing for rebirth
3. Uses can according to water quality requirement:first grade multi-media filter,which can remove mud,rust,colloid and suspension in water.Second grade activated carbon filter,which can remove color,olfactory,biochemistry organic in water and encrease the left oxygen value and pollution in water.Third grade equiped softener equipment.
4. Effluent water capacity achieves the water supply of national low-pressure bioler.
5. Time control- type;flow control- type.In working ,apply single-tank,double-tank and multi-tank etc. other varied combination method.When choosing,users can choose as their needs.In operation,it has not only automatic function,but also is manual operation.
01.What is the capacity(cubic meter per hou)for this water softener?--VERY IMPORTNT for our quotation.
02.What is the working hours for this water softner each day?is it continuous 24 hours working or not?
03.Do you require the whole water softener system be assembed and installed into an integrated compact cabinet?
04.if there is no special requirement on valve brand,we will choose top domestic brand valve,
|Amount of resin(KG)|
operation and respective
use and the other for standby)
Our softeners are effective in:
Preventing scale in the hot water system and around taps
Removing existing scale
Reducing boiler fuel cost and heating system maintenance costs
Preventing soap scum, which is evident around the bath and sink
Improving the texture of laundry by preventing detergent scum deposits within the fibers of clothes, bedding, etc.
Reducing soap and detergent costs.